40W LED 1x4 Troffer Light
40W LED 1x4 Troffer Light
Product Abstract:40W LED 1x4 Troffer Light,LED 1x4 Troffer,LED 1x4 Troffer Retrofit Kit,5200lm,available in 2,700K to 5,700K, Perfect for use in commercial applications such as offices, schools, retail locations, hospitals, and more.Easy-to-install upgrade to LED lighting in existing recessed troffers,replaces traditional fluorescent troffers.
- Product Description
GENERAL DESCRIPTION40W LED 1x4 Troffer Light,LED 1x4 Troffer,LED 1x4 Troffer Retrofit Kit, 5200lm,120W HPS Equiv,available in 2,700K to 5,700K, Perfect for use in commercial applications such as offices, schools, retail locations, hospitals, and more.Easy-to-install upgrade to LED lighting in existing recessed troffers,replaces traditional fluorescent troffers.
STRUCTURE, MATERIALS, & FEATURES1. Beam angle: 120 degrees
2. Incandescent/ MH/HPS/HID/MHL/CFL lamp retrofit
3. Precision Die Cast Aluminum Housing
4. Durale Chip and Fade Resistant Powder Coat Finish
5. Energy saving up to 70%-80%
6. Wide colour availability in degrees Kelvin(K),2700K SW / 3000K WW / 4100K NW / 5000K DW / 5700K CW
7. 50,000 hours, 5 Years Warranty
8. Easy Installation
9. UL listed power supply, ISO CE ROHS listed
Item No. BB-RTGD-40W-A-14-D Rated Watts 40w Input Voltage 100-277VAC/50-60HZ | 200-480VAC available Luminous Flux 5200lm Driver Model
Power Factor >0.95 Beam Angle
Color Rendering Index (CRI)
Ra > 80
Operating Temperature -40 ~ 45 LED Luminous Efficiency >130lm/w Color Temperature 2700K SW / 3000K WW / 4100K NW / 5000K DW / 5700K CW LED Emitter Life 50,000 hours at 25°C Fixture Material Precision Die Cast Aluminum Housing Application Offices, Lobbies, Hallways & Conference Rooms in Schools, Municipalities, Libraries, Airports, Healthcare Facilities, Showrooms, Corporate Campuses, Retailers and Hospitality Environments. The Dimensions L1213mm(47.76in) x W303mm(11.93in)
SENSOR MODULEPIR sensor
1.on @ night light
3.100% on when motion detected(in night).hold time 40"(typical).if no new
Note:1sensor @ 1 lamp only.Dailight sensor
It supplies a simple and effective solution for daylight harvesting.Connecting to
1-10V interface and using photocell to measure ambient lux level and
automatically calculate how much artificial light is needed,and then convert the
amount of light to 1-10V dimmable control gears(ballasts or LED drivers).1-10V
dimmable control gears adjust the lighting output according to the signal from
the daylight sensor.
Note:1sensor @ 20 lamps MaxMicrowave motion available
1.As built-in daylight sensor can read brightness value,the sensor dose not
swith on the light if with sufficient natural light.
2.Switch on the light on detection of movement,and switch off after ahold time
when there is no motion detected.
Note:1sensor @ 10 lamps Max
Normally. The Traditional Tube Light has the ballast or capacitor or ignitor.
Replace Traditional Tube Light1.Remove the Ballast,Capacitor,Ignitor.2.Only need to put the L(live wire),N(null line) connected to the external power supply.T-BAR CEILING MOUNTING
Install the(4) supplied T-Bar clips onto the mounting bracket on the utside of the
housing.See picture 1.
Put the troffer into the T-Bar Ceiling panel and attach the clips on the housing
onto the T-Bar.
Fix the safety cable at the back side of the house to the ceiling incase the troffer
drop down.SUSPENDED MOUNTING
Attach customer supplied cables to the(2) cable slots on each corner of the troffer
housing.See picture 2.
Attach customer supplied cables to mounting surface using customer supplied
hardware.Ensuring that mounting surface can support the luminaire.
1.Connect the RED fixture lead to LINE(+)supply lead.
2.Connect the BLACK fixture lead to the COMMON(-)supply lead.
3.Connect the GREEN/YELLOW GROUND wire from fixture to supply ground.
4.If any,connect VIOLET to 0/1-10V SIGNAL(DIM+)supply lead and GRAY to EUTRAL/REFERENCE(DIM-) supply lead.(see picture 3)
REMARKS:All unused leads must be capped and insulated.
- Related Products